What is the LC1F115 contactor`s locked rotor rating?
Tesys F Line Contactors and Accessories
Locked Rotor ratings apply to devices tested and offered for definite purpose controls. The IEC products are tested to IEC Standards and carry short time ratings. The following are the permissible short time rating from cold start:
1100 Amps up to 10 seconds
640 Amps for 30 seconds
520 Amps for 1 minute
400 Amps for 3 minutes
320 Amps for 10 minutes.