Are the NEMA Type 4/4X/5 stainless steel or NEMA Type 12/3R or NEMA Type 12K safety switches provided with a hub for conduit entry?
HD Safety Switches
Clarification of standard product features
No, watertight hubs should be order separately for field installation.
Type H hubs would be recommended for the Type 12/3R or Type 12K switches. Type H-CP hubs would be recommended for the Type 4/4X/5 stainless steel switches.
Field cut openings are required on the Type 4/4X/5 (suffix DS or SS) and Type 12/3R (suffix AWK) since no knockouts are provided on these NEMA Type switches.
The Type 12K (suffix A) switches are provided with knockouts.