Can the GK2AF01 common mounting plate be used with the TeSys GV2 starter and D-line contactor?
Tesys GV Manual Starter and Protectors
Yes it can. Do not use the GV2AF3 or GV2AF4 combination block when installing the GV2ME or GV2P and the D-line contactor on the GK2AF01 common mounting plate. The user will need to use either the GV1G02 flexible connector or their own flexible conductors.