Can the GV2ME and GV2P manual motor starters be used on a DELTA system?
Tesys GV Manual Starter and Protectors
When used as Manual Motor Controllers, GV2ME & GV2P can be connected to Delta distribution systems up to 600V. (wye systems up to 600V being also compatible). When used as Combination Motor Controllers type E or type F, GV2P (up to size 22 => 25Amps) can be connected to Wye distribution systems up to 480/277V but not to higher voltages or Delta Systems.