What is the withstand rating for 8903 L & LX Lighting Contactors ?
Issue: What is the withstand rating for 8903 L & LX Lighting Contactors ?
Product Line: NEMA Contactor and Starters
Products sold and used in the United States
Cause: Need ratings
The contactor by itself has a 5K withstand rating.
This lighting contactor is suitable for use on a circuit capable of delivering not more than the rms symmetrical current at the maximum voltage shown below when protected by a 25 A UL Listed thermal-magnetic (inverse time) branch circuit breaker having interrupting ratings not less than shown below: 22,000 @ 240V 14,000 @ 480V And, when protected by a 30 A UL Listed Class RK5 branch circuit current limiting fuse having interrupting rating not less than shown below: 100,000 @ 600V