What is the power terminal lug data for the LC1D40, LC1D50, LC1D65, LP1D40, LP1D50, and LP1D65 contactor?
Issue: Identifying power terminal lug data for the D2 style contactors
Tesys D line contactors
Products sold and used in the United States
Cause: Power terminal lug data required
For contactors with screw clamp terminals: stranded cable w/o cable end : One #10-3 AWG or Two #10-4 AWG per terminal. stranded cable w/cable end: One #10-4 AWG or Two #12-2 AWG per terminal. solid cable: One #10-3 AWG or Two #10-6 AWG per terminal.