Why is there no continuity on a GS1 disconnect even with the handle turned to the ON position?
IEC Style Disconnect Switches
The operator is probably turned to the TEST position instead of to the ON position. Check the viewing window on the front of the switch. If a T appears, the switch is in the TEST position. Find the handle mounting instructions and be sure the handle is installed correctly. Detailed trouble shooting instructions are available upon request.