Can a FAL36060G breaker with a GFM100FA ground fault module be used in the FA100 F or S type circuit breaker enclosures?
Issue: Product design
Circuit breaker enclosures
breaker with ground fault module
No. The GFM module mounts to one end of the breaker and causes the length of both together, to be too long for the enclosure. So the FA100F or S type enclosures are too short. They could be used in the OLD KA225F or S enclosure types, BUT the KA enclosure are obsolete, No longer available with no direct replacement. Square D does not actually offer an enclosure anymore for use with both the FA breaker and GFM module.