What is the short circuit current rating of LUB** and LU2B** Tesys U-Line Self-Protected Starters?
TeSys U line Motor Starters
Stand alone withstand, 5 kA.
Group Motor & Tap rating, 65 kA up to 480 volts wye connected.
UL508E using LU9SP0 incoming line phase barrier, 65 kA up to 480 volts wye connected.
UL508E using LUALB1 current limiter module, 130 kA up to 480 volts wye or delta connected or 65 kA at 600 volts wye or delta connected.