Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
Electrical Distribution Equipment
Connect the control wires of proper voltage to the UVR terminals under the accessory cover. Route the wires out the top of the cover through knock-outs.
Constant voltage at the correct level for the device (24V, 120V, AC, DC, etc) should be applied to terminals numbered D1 and D4. Designation for UV trip is MN.
Link to instruction bulletin 48940-22-01:
CTA-ID : 2025182