Do we have a lug for the Powerpact P Frame I-Line breaker that will accept (3) 600 kcmil cable?
Electrical Distribution Equipment
No, we do not have a lug that will accept (3) 600 kcmil for I-Line.
One alternative is to terminate the 600 kcmil cables in a terminal distribution block and come to the breaker with cable rated for the lugs.
Another option is to use the Powerpact R frame breaker, which will accept (4) 600 kcmil conductors per phase.