What are the acceptable mounting positions of the D-Line contactor?
Tesys D line Contactors
Normal mounting in relationship to the vertical plane. Devices can be rotated 180 degrees but cannot exceed +/- 30 degrees forward or backward from the vertical back plane.
Note: The deviation only applies to AC controlled devices; DC controlled devices will operate properly only when mounted in the normal position in regards to the vertical plane, i.e., do not rotate left or right from the normal upright and vertical position.