Can the Class 8502 Type SCG__ contactor be converted to a 8536 starter by adding 9065SDO__ or 9065SS__ overload relay and 9066SC1 external reset mechanism?
NEMA Type S Contactors & Starters
The open style contactor inside can be modified by adding the appropriate overload relay however there are no provisions provided on the enclosure cover for mounting the 9066SC1 external reset mechanism. The solid state overload is only for three phase power systems. While you can add overload relays to the size 00, size 0, and size 1 contactors, you cannot for the size 2 and above.