Contact field service for a paid retrofit, to modify a 600 volt switch to a 240 volt device.
The QMQB1032 has a blank empty section and the present 600V switch will have two switches
If a twin device is OK then the load base needs to be re-located to the 240 volt position and
inter-phase barrier changed. Mounting hardware may be required and service can evaluate this at
Customer needs to contact Schneider Service, this work is not to be done by the customer/contractor.