Do the D-Line contactors have positively guided, or linked contacts?
Yes. The contactor has positively guided or linked contacts. This makes it suitable to use in safety circuits. A good recommendation for monitoring the power contacts would be to use the NC aux contacts in the base device rather than a separate contact block.