Will an FAP circuit breaker fit into an FA type enclosure, such as an FA100A, FA100AWK, FA100DS, FA100F or FA100S?
Issue: Product design
Product Line: Molded Case Circuit Breaker Enclosures
The FAP breakers are NOT listed in the UL procedures to be used in the FA enclosures. They would physically fit, but the FA100_ series of enclosures are marked for Lug-Lug type circuit breakers ONLY (lugs on both the ON and OFF ends). These breakers would have a "L" as the third digit of the catalog number prefix (FAL, FHL, etc).