Are the lugs on the Powerpact P frame breaker lugs approved for use with fine-stranded wire?
Are the lugs on the Popwerpact P frame breaker approved for use with finely stranded wire?
PowerPact P Frame
High strand count wire in use
No, the lugs are not approved for use with fine stranded wire. Only class B or C cable is approved for use in the lugs, and fine-stranded wire is not class B or C.
NOTE: Finely-stranded wire is also referred to as welder`s cable or DLO diesel locomotive cable.