Can QO or Homeline load centers be mounted sideways?
Horizontal mounting of load center
Mounting of enclosure
Space requirements and wire entry
No. Some of the breakers would have their handles pointing down when in the ON position, which would be a violation of the 2002 National Electrical Code Article 404.7. Breaker handles can be up when in the ON position, or sideways, but not down.