Should metal enclosed switches be used for switching purposes? HVL and HVL/cc
While the HVL and HVL/cc switches are rated for interrupting loads, up to their continuous current, the are not designed for switching operations. They have a low number of operations at rated load. Breakers and contactors are more suited for switching operations.