REVISION: The adaptor kits below are obsolete and no longer available. The Powerpact breakers do not have adaptor kits available and cannot retrofit into the obsolete MLN panelboards. Consider replacing the panelboard with a new I-Line panel.
Are replacement branch breakers still available for the obsolete MLN panelboards and switchboards from 1962 to 1968?
MLN panelboards and switchboards sold and supported in the USA through 1962 to 1968.
Are replacement branch breakers still available for the MLN product line:
The panel and breakers (ML) are obsolete. As 1/1/2015, we do offer adapter kits.
FAL and SK4515
KAL and SK4516
LAL and SK4517
MAL and SK4578
The best solution is to replace the complete panelboard and breakers with current products, see Digest 176, Section 9. Note that new panels will not be the same exact size as the older panels, and will likely be larger due to wire-bending space changes over the years. For assistance in selecting replacement products, first gather as many details as possible of the existing equipment. This includes information such as voltage, amps, interrupting rating, number and size of the circuit breakers, type of enclosure, etc. (the attached document below may help). Taking pictures of the complete panel with breakers may also help. Then, contact your local Schneider Electric authorized distributor, or you local Schneider Electric Field Office.