Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
Can a PHG36030G be retrofitted with a HJL36060 breaker at 60 amps . Also, can a PHG36100G be retrofitted with a 200a JJL breaker?
Breaker Bus Plugs
Yes, an HJP36060 or HJL36060 or similar can fit in place of a 30a breaker . Labels are the only issue . Also, a JJP36200 or JJL36200 can be interchanged. Both Powerpact H and J breakers use the same size bus-plug box.