Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
All Altivar 12
Run the drive from 2 command sources
Yes it is possible:
FR1 = LCC
FLO = L1H
This configuration will start the drive from the remote display (the green RUN button) and if we close the contact on LI1.