Is a neutral available for use with the L600AWK that will accept the S432575 Neutral CT?
Circuit Breaker Enclosure
No, not at this time. The enclosure will not be suitable to accept any Netural CT when the L Frame PowerPact breaker is provided with the LSIG function. Consider using either the M or P-Frame breaker enclosures
at this time or an I-Line version for this requirement.