Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
Will the EDPA fixed padlock attachment physically fit onto the EDB-EPD Ground Fault Circuit Breakers?
Applies to EDB, EGB and EJB circuit breakers with suffix EPD
Application of fixed padlock attachment EDPA
The EDPA cannot be installed onto an EDB-EPD ground fault circuit breaker.
The EDPA must be attached to the breaker using slots in each end of the breaker escutcheon.
Standard EDB circuit breakers without EPD suffix (series 2 and higher), have these slots (see picture A below).
EDB-EPD Ground Fault Circuit Breakers do not have these slots (see picture B below), so the EDPA cannot be attached.
Standard EDB Circuit Breakers without EPD suffix, series 2 and higher (slots)
EDPA can be used.
EDB-EPD Ground Fault Circuit Breakers (no slots)
EDPA cannot be used.