Is the Canadian Load Center Catalog number QO8L100RB Service Entrance Rated?
Load Center Ratings
Canadian QO Load centers
Load Center Application
Service Entrance Rating
The Canadian Electric Code requires load centers for Service Entrance Applications to be a Main Breaker, to have the bonding screw factory installed and a Service Barrier that restricts any load wiring to exit or enter the Service Area(or top endwall) of the load center. So the QO8L100RB is NOT Service Entrance Rated.