Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
Issue: Can the 9065 type SF solid state overload relays mount to an 8536 type S starter?
All Schneider Electric products
Products sold and used in the United States
Cause: Can the 9065 type SF solid state overload relays mount to an 8536 type S starter?
Resolution: The solid state overload relays from size 00 to size 1 are the same for separate mounting and replacement/retrofit mounting; size 2 and above use the type ST instead of the type SF and these devices are designed for separate mounting, not for mounting to a starter. The 9065 type ST should be used to mount to size 2 and above starters.
Keywords: separate mounting, solid state overload relay, SSOLR, retrofit, direct mount, replacement