Is the H268 suitable for use as service entrance equipment?
Heavy Duty Safety Switch
This switch is marked as suitable for use as Service Equipment. This switch does not contain a neutral assembly. If a neutral is required for the voltage system, it should be ordered separately. Use H1200SNE4.