Schneider Electric Canada Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What is the maximum number of auxiliary contacts that can be added to each side of an 8702 reversing contactor?
8702SB, 8702SC, 8702SD 2 and 3 pole reversing contactors
There are a different number of auxiliary contacts that can be added to contactor depending on the size
Up to 4 contacts can be added to each side of a 2 or 3 pole, size 0, 1, or 2 reversing contactor. The first two contacts will attach to the contactor viathe supplied mounting bracket. The two additional contacts will attach to the first two contacts with a 6-32 1" screw, no 6 star lock washer, and 6-32 hex nut. If all four contacts are to be used, one return spring from the contactor must be removed. See the instruction sheet supplied with th contacts for instructions.