Schneider Electric Canada Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Can I use a GFCI on the ATV12 ?
GFCI breaker tripping out
Because drives produce high level of leakage current, and depending of the sensibility of the breaker, tripping can occur.
At the start up of the drive, the capacitor bank is charging and we see the peak of leakage current. This peak is higher when there is more than one drive after the breaker.
Also, it's dependant on many installation parameters such as motor cable type, motor cable length, switching frequency, motor, ground connection.
To avoid the random tripping of breaker due to earth leakage it is recommended to use GFCI called full immunized type A "SI" which is reinforced against high frequency leakage current.