Customer is trying to functionality test on a Conext Battery Monitor
Customers who are installing a new Conext Battery Monitor and they want to test the functionality of the unit for RMA.
*Example is for a 48V battery bank (for a 24V battery bank, check for 24V)
1 . Test from point G (V-) to H (V+) - Voltage should be 48V
2. Test from point E (Vm-) to F (Vm) - Voltage should be 48V
3. Check the two inline fuses
4. With a small screw check the input wire connections
If voltage is present to the inverter (48V) and the fuses are good and the wires are properly seated, RMA the unit.