Can the NQ Column Width panel be inverted to top or bottom feed in the field?
Customer has an NQ Colum Width panel and needs to change from bottom to top feed. Can this be done in the field?
NQ, Column width Panelboards
Can the NQ Colum Width panel be changed from bottom to top feed.
The Column Width panel can be inverted in the field from bottom to top fee. The only issue is with a Main breaker originally lugged for Bottom feed (Lugs on OFF Side). The Main does not have the option to move the lugs from the OFF side to the ON side for Top feeding . A new QBM32225TN Main breaker will have to be ordered for ON side Lugs allowing for incoming Top feeding to Panel