Interface Modules for NEMA Starters and Contactors
Is there an interface module for the NEMA contactors and Starters so that the coil can be energized from a PLC or similar device?
NEMA Contactors and Starters - GIC Product
Product Application and Integration
There is no dedicated interface module for these units. The easiest way to accomplish this type of control is to install an interposing relay (such as an ice cube type). The PLC could energize the relay which would in turn pick up the coil.