Can an I-Line Combination Panelboard be inverted for top feed?
Can an I-Line combination panelboard be inverted for top feed?
Circuit Breaker panelboards sold and supported in the USA.
No, an I-Line panelboard cannot be inverted from the way it was built originally as bottom feed, because the I-Line breaker handles will wind up with their handles in the incorrect
On/Off orientation. They must be bottom feed.