Can you land (3) 600 kcmil wire / per phase, to a HCP508612N panel ?
Can (3) 600 kcmil wire per phase be terminated in a HCP508612N panel ?
I Line Panelboard
Yes , (3) 600 kcmil can be landed to the Main lugs. This can be accomplished by removing the bottom endwall of enclosure box and ordering a HC4212DEX(S) surface, or (F) Flush, 12" box extension. This will allow the extra wire bending space, per NEC, to land the (3) 600 kcmil wire/phase on the Main lugs which are able to provide for (4) 3/0-750kcmil/per phase wires.