Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
For a floating array, the MPPT80 uses a wheatstone bridge to look for imbalance between PV- and PV+ to ground. 450kohms or less of impedance from PV- or PV+ to ground are enough to unbalance the bridge and cause a ground fault error signal.
Impedance of the bridge circuit is about 1.6Mohm.