Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
What branch connector is required to replace a Q1B circuit breaker with a QOB circuit breaker in an NQOB panelboard?
SK5668 is the bus finger or panel board connector kit for use when replacing a Q1B branch on the NQOB panel. The kit will accept QOB breakers. This is a 3 pole kit with A, B and C phase connectors. In a 225 amp NQOB interior this kit will allow you to mount 6-poles of breakers whether they are 1 pole, 2 pole or 3 pole breakers. In a 400/600 amp NQOB interior this kit will allow you to mount 3 poles of breakers whether they are 1 pole, 2 pole or 3 pole breakers.
CTA-ID : 767