Where do you connect the load neutral wire on a QO260GFI?
Applies to QO260GFI
The QO260GFI does not have a load neutral connection and is to be used on 240vac 2 wire applications only.
Not to be used on 120/240 vac applications where two hot wires and a neutral is required.
If a 60 amp GFI breaker is needed on a 120/240 vac system, divide the 120/240 vac loads and put the 240 vac loads on the QO260GFI and put the 120 vac loads on a single pole GFI breaker like the QO115GFI