Is the H100XFA Enclosed Molded Case Switch suitable for use in Division 1 and Division 2 Hazardous Locations?
Heavy Duty Safety Switches
NEMA/NEC enclosure ratings
Yes, the H100XFA is suitable for use in Hazardous Locations defined by the National Electrical Code (NEC) for use in Divisions 1 and 2 of the following: Class I, Groups C & D, Class II, Groups E, F & G, or Class III hazardous locations. The device will be marked for Class and Group, but is not required to be marked for Division per NEC 2005 Article 500.8(B)(2) FPN (Fine Print Note).
This device is UL Listed and CSA Certified.