What is the measurement accuracy of the Micrologic 5.0P, 6.0P, 5.0H and 6.0H trip units (including the sensors)?
Applies to the micrologic Power and Harmonic type trip units, (5.0P, 6.0P, 5.0H and 6.0H) and sensors
Voltage (V) 0.5%
Current (A) 1.5%, higher accuracy (1%) can be achieved with special calibration on the current transformer (CT characterization option).
Frequency (Hz) 0.1 Hz
Power (W) and energy (Wh) 2.0% if CT characterization is used then 1.5%