Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Canada Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Control Transformers may experience momentary overloads on high inrush loads
Applies to 9070 T and TF type Control Transformers by SquareD/Schneider Electric
Inductive loads such as Motors, Solenoids, and Transformers may produce high inrush currents when first energized
Transformers are 100% rated devices. As such, they do not have any continuous overload capacity. CPTs are specifically designed for momentary currrent draw in excess of it`s rating for high inrush type loads. For direction on selecting the appropriate CPT for an application, see page 5 of the Industrial Control Transformer catalog, document # 9070CT9901, attached below.
CTA-ID : 2003429